Address: Sitong Boiler Industrial Park, Taikang County, Zhoukou City, Henan Province, China
We know that during the treatment of oil, the residue of the press consists of a mixture of fibers and nuts in an oil factory.
Shells are remnants of the oil refining process and have long been abandoned. Until a cement plant in Malaysia uses shells as biofuel, it mixes with coal to produce heat. Today, many European countries, including the United Kingdom, the Netherlands, Italy and other countries, have begun to try to mix mixed charcoal to provide the energy needed to reduce fuel costs and reduce Carbon dioxide emissions.
Large oil plants use the fibres and shells of nuts recovered to ignite steam boilers in order to produce electricity and to provide steam in the oil mill. The overheated steam is then used to train turbines to generate electricity for the plant. Compared to other industry residues, it is a good quality biomass fuel with a uniform size distribution, easy handling, easy crushing and limited biological activity due to low moisture content. As a result, the use of the hull as a fuel in an oil production plant can significantly reduce the cost of fuel.
WNS Oil & Gas Fire Tube Boiler
Fuel :Heavy oil, diesel, natural gas, lpg, etc.
Application : Medicine, chemical, light industry, textile, building material, food processing, laundry, hotel, etc.
Brief Intro :WNS boiler is a safe and high efficiency (98%) heating equipment with high automation, it is fast assemble boiler with flue gas three pass and wet back structure, widely used for industrial production.
1.Determine the capacity of the boiler. The boiler capacity should based on the Heating Load Curve or Heat Balance Diagram, and includes the heat loss in pipelines, self-used heat of boiler room, available used waste heat. While, usually, it is difficult to get the Heating Load Curve, the heating load could get based on the max thermal consumption per hour within production/heating/domestic, and then determine by using the coefficient.
2.Determine the boiler efficiency. In order to benefit for economic management, the boilers should have high thermal efficiency, and the boiler output, quantity and other performances have to adapt to the change of heat loading.
3.Determine the boiler heating parameters, including pressure, temperature, etc.
4.It is better to select the boilers with same capacity or combustion equipment. If different, the max limitation is two models, to decrease the problems of equipment layout and management.